Endeavor 6kVA Rack On-line Uninterruptible Power Supply
True on-line UPSs for sensitive electronic equipment and critical servers, network devices, and phone systems
Redundant N+1 and Parallel Configurations
Minuteman® 6kVA On-line Rackmount UPS
- Simple parallel installations (no extra PCB
- Full digital signal processor
- Easy-to-set user personalization
- Intelligent self diagnosis
- Smart fan control
- Emergency Power Off (EPO) function
- True double conversion on-line technology
- High input Power Factor and low voltage THD
- Energy efficient UPS
- LCD/LED panel
- 2X customer options slots
- Smart ECO
- i-Batt (automatically manages end of discharge voltage according to load capacity)
- Cold start function
- Communication capability
- Remotely test the major operating functions of UPS
- Communicate via SNMP/Web card
- Access UPS via the Internet
- Data centers
- Server racks
- Large network switches
- Total rack tower support
- Large PBX systems
6kVA On-line UPS Features
- True on-line architecture supplies critical device
with transient-free pure sine wave AC power
- LCD/LED front panel displays status of UPS
- Switches to bypass automatically in case of overloading at 150%
- Maintenance free sealed-type battery minimizes after-sales service
- Intelligent, temperature-controlled
- Maintenance bypass
- Galvanic isolated transformer
Endeavor 6kVA true on-line rack mount ups
MAIN CONTROL MODULE - ED6200RM
The Main Control module takes only 2U in rack height
and provides 208/240V input and output. Input is hardwired
to the unit. The main control module has a LCD/LED display.
Each control module must have at least one battery back
(EDBP6000RM). Parallel functions are available for up to 208V
24kVA. N+1 full-redundancy function is available up to 18kVA for
208/240V applications and 6kVA for 120V applications. Optional
receptacle boxes are available for 6kVA units.
TRANSFORMER MODULE - ED6000RMXFMR
The transformer module steps down the 208/240V input to
120/208/240V output, takes 2U in rack height, and requires a
control module (ED6200RM), and Battery Pack (EDBP6000RM) to
work. It has an internal bypass switch for single 6kVA installations
(Not available on parallel installations). It handles 208/240V input
and 120/208/240V output.
BATTERY PACK MODULE - EDBP6000RM
Each battery pack module (EDBP6000RM) occupies 3U
in rack height and requires a control module (ED6200RM) to
operate. Multiple battery packs can be daisy chained. Only one
receptacle box can be attached to a battery pack module.
Battery packs are charged through the main UPS.
In addition to a stand-alone configuration, the Endeavor
6kVA rackmount UPS can be configured as:
- Parallel for capacity (12, 18 and 24kVA output load)
- Redundancy (N+1) (6, 12, and 18kVA). This allows all
of the load to be shifted to the other UPS units when
one is taken offline. Configurations using more than two
control modules will require a parallel kit and an external
maintenance bypass switch.
NOTE: 120V output from the Endeavor 6kVA rackmount UPS is
available only in a 6kVA stand-alone configuration or a Parallel
for Redundancy (N+1) 6kVA 208V/240V input and 6kVA 120V
output made up of two ED6200RM control units, two EDBP6000RM
battery packs and two ED6000RMXFMR transformers.
PARALLEL FOR CAPACITY CONFIGURATIONS
This configuration uses mirrored Endeavor 6kVA
rackmount UPS system to achieve higher than 6kVA loads.
Currently, parallel capacity configurations can be used
to accommodate output loads of 12, 18, and 24kVA for
Parallel for Capacity Configuration Table
|Output Load ||12kVA|
|Rack height|| 10 U|| 15 U|| 20 U
|EDBP6000RM Battery Pack||2||3||4
|ED6-PARALLEL Parallel kit||1||1||1
|External Maintenance Bypass Switch||1ED6-MTBS2||1ED6-MTBS4||1ED6-MTBS4
REDUNDANCY (N+1) CONFIGURATIONS
This configuration is used to provide redundancy
backup. When one UPS is taken offline, this configuration
allows the load to be redistributed to the remaining UPS
Redundancy (N+1) Configuration Table
|Input||6kVA ||6kVA ||12kVA ||18kVA|
|Output Voltage||120 and 208/240V||208/240V||208/240V||208/240V|
|Rack height||14 U ||10 U||15 U ||20 U|
|EDBP6000RM Battery Pack||2||2||3||4|
|ED6-PARALLEL Parallel Kit||1||1||1||1|
|External Maint.||1 ED6-MTBS2||1 ED6-MTBS2||1 ED6-MTBS4||1 ED6-MTBS4|
|* Use ED18000RM part number||** Use ED24000RM part number|
OPTIONAL RECEPTACLE BOXES
Two receptacle boxes are available. One for
208V/240V output only (ED6-208RB) and one for both
120V and 208V/240V output (ED6-120RB).
208V-Only Receptacle Box- ED6-208RB
Receptacles: (1) L6-30R, (1) L6-20R and (4) 6-15/20R. Only
one receptacle box can be connected to a battery
120V/208V Receptacle Box - ED6-120RB
Receptacles: (1) L6-30R, (1) L5-30R, (1) L5-20R and (2)
5-15/20R. Only one receptacle box can be connected to
a battery pack.
COMMUNICATION AND SOFTWARE
The Endeavor 6kVA UPS includes SentryPlus power management software and can optionally use either the SNMP-NET for ED6&10KVA
card or the SNMP-SSL for ED6&10KVA & PRO-RT card.
The Endeavor 6kVA UPS uses a battery pack
(EDBP6000RM) that contains sealed, non-spillable,
maintenance free, value regulated, lead acid batteries.
The UPS module does not have internal batteries. Typical
recharge time for the battery pack is 8 hours from total
The battery pack contains (20) 12V 7.2Ah batteries.
Runtime at full load is 9 minutes. At half load the
runtime is 23 minutes
WHAT THE FUTURE HOLDS...
Parallel Configurations: All current
6kVA products are compliant with parallel
configurations when these options are
available. In the relatively near future you will
be able to configure your Minuteman Endeavor
6kVA into a parallel configuration increasing
system capacity up to 24kVA.
- Input and output will be hardwired
- A parallel kit will be required
- It will contain all the required RJ-45 cabling and an instruction
- It is required that a maintenance bypass switch
ENDEAVOR 6KVA UPS LED/LCD
FRONT PANEL DISPLAY/CONTROL
The Endeavor 6kVA UPS multi-functional LCD/LED panel will
display various states of the UPS. The LED display will show the
UPS working status, Utility Status and UPS Abnormal status. The
LCD display will show the Input/Output voltage, frequency, load
status, internal temperature, and faults.
Configuring the UPS parameters are done through the LCD.
MAINTENANCE BYPASS SWITCH
The maintenance bypass switch removes the requirement to
power down the UPS to perform routine maintenance, replace
batteries or to change battery configuration, The maintenance
bypass switch is usually mounted adjacent to the UPS, enabling
the UPS to be isolated from the load without interrupting power
to essential applications.
- Maintenance bypass switch
- Galvanic isolated transformer for 120V applications.
- Parallel kit